This is the printer friendly version of the Greenhouse Heatsink Connection Diagram article from the Renewable Energy Website REUK.co.uk.
Click here to print this article.
Printed at 09:56pm 23rd May 2013
Greenhouse Heatsink Connection Diagram
Putting together a solar powered greenhouse heatsink system
In our article Solar Greenhouse Heat Sink (1) we introduced a simple method of keeping a greenhouse frost free at night, and also a little cooler in the day when it can otherwise get too hot.
In this article we will look in more detail at how the electrical (2) part of the system is put together and how the solar panel, battery, and fan should be selected.
Pictured above is a 12V DC Fan which is rated at 0.070 Amps (0.84 Watts). Available in the UK for around £5.00, such a fan is perfect for this application. With brushless contacts and high quality bearings, it is rated to last at least 50,000 hours (almost 6 years of continuous use) without overheating. It can also push through a lot of air while drawing a very low current making it optimal for use with a PV solar (3) powered system.
NEW Click here to for more information and to purchase this 12V 0.84W Fan (4) now from Rapid Online (5).
Voltage RegulatorWhen fully charged a lead acid battery (6) will reach over 13.5V, and when under charge can reach well over 14 Volts. If a 12V fan is powered with more than 12 Volts, then it will spin faster, get hotter, use more power, and fail much faster. Therefore, it is recommended that an LM2940 12V regulator (7) is used. This gives a fixed 12.0V output from input voltages in excess of 12.5V (virtually flat battery), and 0.5V less than the input voltage if it is less than 12.5V. Click here to view details of the easy to use 12 Volt Regulator (8) circuit which we sell in the REUK Shop (9).)
The Solar PanelThe Solar Panel should be chosen to match the power consumption of the fan. A fan rated at 0.070 Amps uses 24 x 0.070 = 1.68 Amp Hours (Ah) of electricity per day. Therefore, the solar panel must put at least 1.68 Ah into the battery every day, plus an extra 20% to cover losses. 1.68 x 130% = 2 Ah.
Obviously a solar panel does not generate its rated power 24 hours per day. Once you take into account nighttime, bad weather, and early mornings and evenings when the sun is low in the sky, there are not many hours of real generating time. For the UK you can expect an average of the equivalent of 4 hours at the rated power per day, therefore the power rating of the solar panel should be six times greater than that of the fan. With our example fan rated at 0.84 Watts, we need a solar panel rated at 5 Watts = 6 x 0.84. (Click here for more information about the 12V 5W Solar Panel (10) pictured above).
Depending on the exact geographical location of the greenhouse - further north in the northern hemisphere means less solar electricity generation, the quality of the battery used, and the position of the solar panel, additional solar capacity may be necessary to make up for shortfalls and losses in the system.
The battery is the third and final key component of the greenhouse heatsink system. An old car battery can be used (available free of charge), but will not retain charge well - therefore more PV solar panels will be required. Ideally a suitable deep cycle (11) (leisure) battery should be used. This will hold charge well - e.g. self discharge of below 3-5% per month - and will cope with being discharged deeply.
If a very small battery is used, a solar charge controller (12) will be necessary to prevent overcharging. In addition, there will be insufficient stored charge to cope with multiple overcast days. Instead it is usually better to match the battery to the solar panel to ensure that there is enough stored charge capacity for the fan to be powered even if it is cloudy for a week. With a 5 Watt solar panel and a 0.84 Watt fan, something of the order of at least 15-20Ah would be perfect.
NEW Click here to read our new article 12V Deep Cycle Batteries for Solar (13) for more information on selecting and purchasing suitable batteries for this application.
Putting the Greenhouse Heatsink System TogetherThe final components of the system are a suitable fuse holder and fuse (14) (use a 2 Amp fuse for a 0.84W fan to protect against short circuits etc), and a switch (15) so that you can manually switch off the system if the battery is flat to give it a chance to recharge.
The fuse should be positioned as close as possible to the positive terminal of the battery to make it most effective. The on/off switch should be positioned between the battery and the voltage regulator (rather than between the regulator and the fan) so that no power is wasted when the system is switched off.
Web Link References(1) http://www.reuk.co.uk/Solar-Greenhouse-Heat-Sink.htm
Article from REUK.co.uk:
Published: 31st March 2009
© REUK 2013